|Surface Resistivity P.T.P.||ASTM D257||< 5.5 x 107 ohms|
|Resistance to Ground||EOS-ESD 7.01||< 1.0 x 106 ohms|
|Combination Resistance Person / Heel Grounder/ Flooring||ANSI/ESD STM97.1-2006||< 3.5 E07|
|Charge Decay Time||FTMS 4046-101c||<<< .17 seconds|
|Flammability||Radiant Panel ASTM E648||.73W/cm², Class I|
|Residual Indentation||LF-475A||.002" average|
|Abrasive Wear, Taber 1000 gm weight||H-18 wheels, 5000 cycles||1.1% loss of weight|
|Abrasive Wear, Taber 1000 gm weight||H-18 wheels, to wear layer penetration||> 20,000 cycles|
|Static Coefficient of Friction||ASTM D-2047-03 James Test||.5 approx|
|Static Load Limit||DIN 16961.2||> 700 p.s.i.|
|Meets or exceeds minimum requirements of
Federal Specifications for flexibility, dimensional stability, resistance to reagents and residual indentation
Installation & Maintenance
Install only on approved sub-floor surfaces
Follow detailed installation instructions.
Installation of ESD Static Control Solid Vinyl Flooring.pdf PDF format (2,580KB)
Install only on sub-floors which have a permanent Moisture Barrier and are dry < 3.0 lb/1000 sft. vapor emissions; 85% rH and with a pH of 7-9 per Moisture Limitation Specification
loose lay as mats
Install with Sigaway® Electronic full surface conductive dry adhesive or with Sigaway® Original regular dry adhesive with Siga Circuit seam bridging tape.
Install with UZIN KE 2000 SL water based acrylic conductive adhesive.
Install with Sigaway® Electronic full surface conductive dry adhesive or with Install with UZIN KE 2000 SL water based acrylic conductive adhesive.
Permanently glued rolls must be heat welded
Heat-welding is optional for tiles
Follow detailed maintenance instructions.
Cleaning Instructions for ESD Static Control Flooring PDF format (133KB)
Limited warranties vary by product, and are applicable only if materials are installed professionally on suitable and approved sub-floors Concrete Subfloors and Moisture Testing with approved adhesives and within the approved moisture limits, on sub-floors which have a permanent Moisture Barrier and are dry < 3.0 lb/1000 sft. vapor emissions; 85% rH and with a pH of 7-9 per.