AZO ESD Conductive Berber Details
|Surface Resistivity P.T.P.||ASTM D257||< 7.5 x 106 ohms|
|Resistance to Ground||EOS-ESD 7.01||< 1.0 x 106 ohms|
|Charge Decay Time||FTMS 4046-101c||<<< .17 seconds|
|Flammability||Radiant Panel ASTM E648||.73W/cm², Class I|
|Noise Reduction Coefficient||ASTM 423-90||NRC .25 approx.|
Installation & Maintenance
Follow detailed installation instructions.
Installation Manual PDF format (151KB)
Install only on sub-floors which have a permanent Moisture Barrier and are dry < 3.0 lb/1000 sft. vapor emissions; 85% rH and with a pH of 7-9 per Moisture Limitation Specification
loose lay as mats
Install with Sigaway® Electronic full surface conductive dry adhesive or with Sigaway® Original regular dry adhesive with Siga Circuit seam bridging tape.
Install with Uzin KE 2000 SL water based conductive adhesive.
Tiles: Install with full surface Sigaway® dry adhesive
Install with Uzin KE 2000 SL water based conductive adhesive
No special seaming adhesive needed
Follow detailed maintenance instructions.
Maintenance Instuctions PDF format (118KB)
Limited warranties vary by product, and are applicable only if materials are installed professionally on suitable and approved sub-floors Concrete Subfloors and Moisture Testing with approved adhesives and within the approved moisture limits, on sub-floors which have a permanent Moisture Barrier and are dry < 3.0 lb/1000 sft. vapor emissions; 85% rH and with a pH of 7-9 per.